Strona wtórna:

1103 Measurement: Full Scale Voltage (100%) 220,0 kV 
1104 Measurement: Full Scale Current (100%) 1200 A 
1105 Line Angle 82 ° 
1211 Angle of inclination, distance charact. 82 ° 
1111 Line Length 47 km 
1116 Zero seq. comp. factor RE/RL for Z1 0,00 
1117 Zero seq. comp. factor XE/XL for Z1 0,50 
1118 Zero seq. comp.factor RE/RL(> Z1) 0,00 
1119 Zero seq. comp.factor XE/XL(> Z1) 0,00

k0 = 0,4951 (dopisał RL)
fi_k0 = 8 st. (dopisał RL)
k1,2 = 0 (dopisał RL)
fi_k1,2 = -82 st (dopisał RL)



1301 Operating mode Z1 Forward 
1302 R(Z1), Resistance for ph-ph-faults 8,00 Ohm 
1303 X(Z1), Reactance 8,95 Ohm 
1304 RE(Z1), Resistance for ph-e faults 22,00 Ohm 

1351 Operating mode Z1B (overrreach zone) Forward 
1352 R(Z1B), Resistance for ph-ph-faults 8,50 Ohm 
1353 X(Z1B), Reactance 12,11 Ohm 
1354 RE(Z1B), Resistance for ph-e faults 22,50 Ohm

1311 Operating mode Z2 Forward
1312 R(Z2), Resistance for ph-ph-faults 9,00 Ohm 
1313 X(Z2), Reactance 15,93 Ohm 
1314 RE(Z2), Resistance for ph-e faults 23,00 Ohm 

1321 Operating mode Z3 Forward 
1322 R(Z3), Resistance for ph-ph-faults 11,00 Ohm 
1323 X(Z3), Reactance 36,22 Ohm 
1324 RE(Z3), Resistance for ph-e faults 24,00 Ohm